|Capacity||100gms/hr to 5 Kgs/hr of chlorine|
|Fluid Media||Chlorine Gas|
|Accuracy||+ - 4% of Max Flowmeter capacity|
|Voltage||240 V AC or 24 V DC|
The Industries that benefit Chemicals and Fertilizers, Refineries, Petrochemicals, Power stations, Steel Plants, Cement Plants, Pharmaceuticals, Industries, Pesticide Industries, Food Industries, Textiles, Paper and Pulp Industries,Sugar Plants, Municipalities, Corporations, Townships, Water Boards, Theme Parks, Hotels, Apartment Complexes, swimming pool water distubution system etc.
Principle of Operation
Motive Water (water at high pressure) passes through the injector to produce vacuum. This vacuum extends upto Vacuum Regulator. The chlorine gas received (from Tonnes / Cylinders under pressure this regulator is in build regulating system when we control the flow of chlorine through flow control valve the pressure regulate automatic and gas flow through a Rotameter to injector where chlorine and water mixes .
Safety Valves - The system is provided with Pressure Relief Valve. Vacuum Relief Valve, Check Valve and Emergency Drain Relief Valve.
Flow control valve
MOC :- PVC/PVC FRP
Material supplied with system